|Sl. No.||Zone||400 KV Station||220 KV Recieving Station||110/66/11 KV Sub-Station||From||To||LC Duration (In Hours)||Reason For LC||Areas Affected||Request Type|
|24/08/2019 08:00:00||25/08/2019 18:00:00||34||LC for 220kV (BWSSB) Harohalli - Kanakapura SC line.
LC required for the works of shifting of existing 220kV S/C Harohalli - Kanakapura line passing over M/s KIADB Plot No. 283, KIADB Harohalli I/A 2nd Phase Kanakapura. Work involved is erection of 3Nos of 220kV DC towers in the existing corridor with stringing of 3 spans of drake conductor & dismantling of 3Nos of towers.
During LC period 220kV kanakapura R/s (128MW) supply will be fed from 220kV TK Halli R/s.||Nil.||emergency|
|24/08/2019 10:00:00||24/08/2019 17:00:00||7||LC required for the work of:
Line of 66kV Yarandanahalli-Suryacity & 66kV Yarandanahalli-Anekal.
For erection of 2Nos 66kV MC towers & stringing of Drake ACSR conductor (2spans) & releasing of existing DC towers and coyote conductor.||SuryaCity, Anekal Taluk.||emergency|
|3||NELAMANGALA||Select All, A station, EDC||Austin Town||24/08/2019 10:00:00||24/08/2019 17:00:00||7||Lc required for 66/11kV Austin Town S/s.
LC required to carry out the following works.
1. Repairing & alignment of GOS of Koramangala Y-Phase.
2. Servicing of 66kV EDC line BUS GOS.
3. Attending Oil leakage.
4. Attending Hot line observations.
5. Weak conductor replacement of Tr-1 bay.
6. Urgent Maintenance works as per maintenance manual.||Areas feeding from 66/11kV Austin town S/s.||emergency|
|4||SOMANAHALLI||Kanakapura, Somanahalli, T.K.Halli||AO SMITH-EHT|
EHT-Bhurauka gases Ltd
New India Gypsum-EHT
Orchid laminations -EHT
|25/08/2019 08:00:00||25/08/2019 18:00:00||10||LC for 66kV Somanahalli - TK Halli line 1&2.
LC required for Shifting of S/C 220kV line at M/s KIADB Plot No. 283, KIADB Harohalli I/A 2nd Phase Kanakapura. Work involved is erection of 3Nos of 220kV D/C towers in the existing corridor with stinging of 3spans of drake conductor & dismantaling of 3Nos of towers.
Note: To provide Power supply
during LC period 66kV Jumps to
be removed at 3 places:
1. At step down tower for V.R. Doddi BWSSB line-2
2. At Jakkasandra village for TK. Halli - BWSSB line-1.
3. TA step down tower for Somanahalli - Harohalli BWSSB line-2.
Power Supply will be affected to the connected S/s & EHT installations at time of removing & providing jumps (2 times) for 2Hrs in each operation.||Areas feeding from 66/11kV Guruvinapura S/s, V.R.Doddi S/s & EHT installations, M/s Bhoruka Gases, M/s A.O.Smith, M/s Orchid Laminates, M/s India Gypsum.||emergency|
|5||HOODY||220kV EPIP, HSR Layout, Hoody||EPIP|
|31/08/2019 09:00:00||01/09/2019 18:00:00||33||LC required on 220kV Hoody -HSR and 220kV EPIP - HSR Layout DC line. LC required for carring out of following works: For erection of 3Nos of 220/66kV MCMV Monopole tower & stringing of AAAC Moose & Drake ACSR conductor & ground wire (4 spans (24 Conductors)) for the work of shifting of existing 220kV Hoody -HSR and 220kV EPIP - HSR Layout DC line and 66kV EPIP-Divyashree Tech Park & EPIP-Kachamaranahalli line by using 220/66kV MCMV design based Monopole towers & AAAC Moose conductor in the Premises of M/s. QUALCOMM Pvt, Ltd., at EPIP, B'luru (E) Tq, B'luru under self-execution basis.||-||emergency|